4D Service Group is not only passionate about providing exceptional domestic water booster pump service, but we are also passionate about conserving our planet. In the last few years we have recycled about 14 tons of material--including all sorts of metal, motors, drives, and many other recyclable materials. We believe we can make the world a better place by recycling.
14 Tons of Material Recycled!
Recommended DWBP Hurricane Procedures
Under Evacuation Orders (Voluntary or Mandatory) or Power Loss Conditions:
Always check with your DWBP specialist first.
Step 1: Turn off the power to the panel (disconnect knob on front of panel).
Step 2: Close all the valves on the system to isolate the building from the city water supply in order to protect from potential contamination from the city/county.
After the storm has passed and power has been restored (generator or electric company):
Step 3: Test water purity or check with city/county water supply for verification of water safety. Once water has been cleared safe, SLOWLY open all valves on the system that were previously closed.
Step 4: Turn on power to the panel (disconnect knob on front of panel). Once panel is powered up the system will start a "Pressure Recovery Mode" and the building should be pressurized within minutes.
4D Service Group Specializes in Domestic Water Booster Pump maintenance and installation.